Wire still hot after breaker turned off
The 15A breaker was turned off and I proceeded to tap into the box for an additional light. It was still hot. I turned it on and off again and one time it was off and another time the tester's light dimmed slowly to off. Could it be a bad breaker or possibly a loose connection on this breaker at the panel causing this?